LPR – Lock Position Return
AC – Alternating Current / Wechselstrom (z.B. 230V)
DC – Direct Current / Gleichstrom (z.B. 24V)
NO – Normally Open
NC – Normally Closed
HI – Switch direction of rotation I
HII – Switch direction of rotation II
SI – Additional switch direction of rotation I
SII – Additional switch direction of rotation II
The direction of rotation I, II is indicated on the EWA (see control unit setting figure step 3)
( 4 ) Use the drill to rotate the shaft in direction of rotation ’I’ until you have reached the desired limit position (see direction of rotation arrow on housing beside the output shaft). It is also possible to start with the limit position for ’HII’ (see Step 5). Once the desired limit position has been reached, save limit position ’HI’. To do this, hold down button ’S’ and also press button ’HI’ until LED ’HI’ changes from red to green.
( 5 ) Once the limit position for ’HI’ has been set, rotate the drive in the opposite direction, as described above, into limit position ’II’ (see direction of rotation arrow beside the output shaft). Once the desired limit position has been reached, you can save limit position ’HII’. To do this, press and hold down the ‘S’ button while also pressing the ‘HII’ button until LED ‘HII’ changes from red to green.
( 7 ) Connect up the drive to the power supply unit. Fit the cover and the rubber gasket using the 4 screws and the 4 copper washers provided.Then connect up the electrical power supply and start up the unit (test run) in accordance with the instructions in the EWA Operating Manual (Electrical connection, Chapter 6 ff. and Initial start-up, Chapter 6.5)